26 April 2023
As mentioned in a previous update, Type AC RCDs must not be installed in Australia after 30 April 2023.
Western Power have published the following communication about the upcoming change.
RCD type changes effective 30 April
As stipulated in AS/NZS 3000:2018 Wiring Rules clause 18.104.22.168.2, Type AC RCDs must not to be installed in Australia from 30 April 2023.
This means any Preliminary/Notice of Completion submitted after this date will require the fitting of the Type A RCD to help with the protection of circuits containing both AC and DC operated equipment with electronic components.
Type A RCDs are designed to operate on both residual sinusoidal alternating current and residual pulsating direct currents. This requirement also applies to builders power pole supplies as they’re regarded as an installation and electronic components used by the building industry are plugged into these poles.
The preface of AS/NZS3012:2019 also mentions that this standard is to be used in conjunction with:
The following symbols can be found on an RCD to indicate the RCD type.
What type of RCD?
If you have any questions feel free to contact us.
Customer Services team